The key use of high energy igniters is the basic principle of capacitor energy storage charge and discharge, which is widely used in industrial boilers, petrochemical plants, coal chemical industry, natural gas, steel metallurgy, and other fields.
Its working principle is: select an AC current with a voltage of 220V and a working frequency of 50HZ, raise the voltage to over 2500 volts according to a step-down transformer, and charge the energy storage capacitor battery after passing through the rectifier. When the battery charging voltage exceeds the penetration voltage of the discharge tube, the voltage in the energy storage device is charged and discharged according to the ignition cable and conductive rod of the discharge tube. Xuzhou Jieneng Power Equipment Co., Ltd. charges and discharges semiconductor material nozzles, When both sides of the nozzle are exposed to a single pulse voltage with a high kinetic energy value, a strong spark discharge is generated on the surface of the semiconductor material as an open flame for ignition.
Do you understand?
If the high-energy igniter fails to ignite due to abnormal conditions, what should be done?
Understand the fault phenomenon first: Is the system software switched on or off? Poor contact between cable and igniter or ignition gun? Short circuit or short circuit in the cable? Damaged ignition gun? The igniter is damaged?
Therefore, it is necessary to: 1. Check the input switch power supply plug; 2. Check that the release between the igniter and the ignition gun is in good contact with the ignition cable; 3. Remove and replace the cable or ignition gun or igniter.
When using a high-energy igniter, it is necessary to pay attention to the following matters: 1. When igniting, first turn on the ignition equipment, and then ignite the oil pump (gas). Generally, the ignition duration should not exceed 30 seconds; During ignition, the combustion air should be turned down and gradually increased after the ignition; 3. Gasoline and diesel fuel shall be atomized well, and poor atomization quality may harm the ignition pass rate; 4. During the operation of the ignition equipment for 30 seconds, it is necessary to rest for 1 minute before changing to prevent continuous long-term use.
The above is the knowledge content about high-energy igniters that I have brought to you. If you are interested in other content, you can also consult my editor, who will continue to update it for you.
Tel: 0516-81915686 Fax: 0516-81915687
Website: www.jinengdianli.com Email: email@example.com
Headquarters address: No. 6, Software Park Road, Quanshan District, Xuzhou City, Jiangsu Province
Manufacturing base: No. 2, Fumin Road, High tech Industrial Development Zone, Xuzhou City, Jiangsu Province